MODES OF THE WORK OF THE RECONSTRUCTIVE INSTALLATION OF HOT WATER SUPPLY OF THE MICROREGION AT THE CONSTRUCTION CONNECTION
The housing and communal services of Ukraine consume about a quarter of the country's fuel and energy resources. The main factors determining unproductive energy losses in the construction industry are the imperfection of the technical systems of heat supply and equipment of buildings, the inefficient use of bulky planning and design solutions, the use of enclosing constructions of buildings with a low level of thermal protection. The results of calculations of thermal regimes of the hot water supply installation at two-step mixed circuit for connecting heat exchangers to heat networks. On the example of the district heating system of the residential district, the influence of the conditions of work of hot water heaters on the amount of cost savings of network water with the use of additional thermal insulation of structural elements of buildings is shown. The method of determining the flow of network water through heat exchangers of hot water supply due to the reduction of the calculated heating load when applied additional insulation on the protective structures of functioning buildings is developed. The research is to assess the influence of heat exchangers of hot water supply in the two-step mixed flow diagram for connection to the consumption of network water for heating insulated buildings. The results of calculations have shown that in conditions of connected heat supply, with the provision of new, lower thermal power consumption by buildings, the decrease of the temperature of the coolant at the inputs to the heating system, the effectiveness of the additional insulation of the fencing of the structures depends on the operating conditions of the hot-water installation of hot water supply. It was established that the reduction of the economic effect of additional "insulation" of functioning buildings is due to the need to increase the cost of heating heat-carrier through heat exchangers of the second stage of the heating installation of hot water supply. For the considered microdistrict, the deterioration of the effect of reducing the cost of network water is about 30% of the cost savings of the coolant for heating, characteristic of unconnected heat supply.
Keywords: centralized heat supply, heating hot water supply units, two-step mixed connection of heaters, energy saving, insulation of enclosing structures of buildings.
How to Cite
The authors who publish in this collection agree with the following terms:
• The authors reserve the right to authorship of their work and give the magazine the right to first publish this work under the terms of license CC BY-NC-ND 4.0 (with the Designation of Authorship - Non-Commercial - Without Derivatives 4.0 International), which allows others to freely distribute the published work with a mandatory reference to the authors of the original work and the first publication of the work in this magazine.
• Authors have the right to make independent extra-exclusive work agreements in the form in which they were published by this magazine (for example, posting work in an electronic repository of an institution or publishing as part of a monograph), provided that the link to the first publication of the work in this journal is maintained. .
• Journal policy allows and encourages the publication of manuscripts on the Internet (for example, in institutions' repositories or on personal websites), both before the publication of this manuscript and during its editorial work, as it contributes to the emergence of productive scientific discussion and positively affects the efficiency and dynamics of the citation of the published work (see The Effect of Open Access).